A notification will be generated if the feedback voltage is at least 0.5v different from the output voltage.
If an economizer position failure notification is generated, you can compare the output position against the feedback position through the thermostat’s history graph.
- Navigate to your Pelican web-app.
- Either select Notifications and select the economizer position failure notification or select the group the thermostat is in.
- Select the thermostat.
- Select History Graphs.
- You will see Economizer (output) position graphed in green and Feedback (actual damper position) graphed in grey.
Note: The feedback position will only graphed when it is at least 0.5v different from the output voltage.